Category : Chiller Technology
Air cooled chiller condenser maintenance at Maximus Chillers. The condensers in the picture are a row of 6. These are remote from a row of 6 chillers, located in a plant room in the building below. The chillers are 750 kw single screw compressors with a control panel located to the side of each. On this visit, the emphasis of the maintenance was scheduled as being to the condensers.
Fan Speed Controllers
The refrigerant for the systems is R134a, so to allow for the saturation of the refrigerant, 8 bar is the head pressure set point. This pressure corresponds to the desired condenser temperature of 36°. Subcooling of 6° to 8° is achieved during the nominal operation of the plant. Each fan speed controller runs the 12 condenser fans together. Other condenser designs where fans bang on forwards and backwards cause vibrations resulting in reoccurring leaks on the condenser. Chiller No. 2 had tripped during a “discharge override” system message. On inspection of No. 2 condenser- the fans speed inverter had tripped on “over temperature” alarm. The panel fan, which is the kind to cool computers, was found to be still trying to run but seized. This failure had caused the alarm on the inverter. The panel fan was replaced from the stock of parts in the on site stores. The chiller was reset and a detailed Tick Sheet was completed noting the occurrence of this fault on arrival.
0161 370 7193
Air Cooled Chiller Condenser Wash Down Maintenance
Because of the large size of the plant, the customer had installed a fireman’s hose for the wash down of the condensers during air cooled chiller maintenance. This is located in the free space beneath the condensers. It is fitted to a portable buggy so it can be moved under each condenser. Setting the nozzle to the correct attitude, our engineer moved the buggy sideways, so as to rinse the condenser in the direction of the fins. The condenser was relatively clean as the on site maintenance engineers carry this task out as part of their scheduled maintenance.
To read more about air cooled chiller maintenance click the Tag at the top of the page.
Air Cooled Chiller Planned Maintenance
Read more about HVAC air coils on Wikipedia | Click Here