Chiller compressors fail often the result of ineffective servicing and system testing.
News Article No.4
At Maximus Chillers, we carry out extensive tests during our visits to ensure that small problems are resolved before they become big problems. If we notice a reading starting to become abnormal, we can carry out the diagnosis, then do the necessary service. Some of the compressor readings we monitor:
The suction, discharge, motor windings and bearing temperatures are recorded for comparison to previous visits. These are often available in the PLC for the chiller, or our engineer can take the readings with his test equipment. Problems with the oil system can be the cause of higher compressor temperatures, the system running outside of its nominal operating conditions is another reason. Magnetic drive systems have an advantage as they do not use oil.
Portable vibration sensors are carried in of each of our company vehicles. This is an accelerometer to measure vibration. Along with other system readings, we keep an on going record of the vibration levels around the compressor. When internal components are coming out of alignment due to wear, this causes an out of balance condition in the compressor. This, in turn, causes a knock on effect- causing other components to go out of balance. Catching this condition early will prevent a compressor smash up resulting in the replacement of expensive internal components.
Another way of preventing big problems to occur is periodic compressor oil testing. Samples are taken, usually on alternate visits, which are sent off to a laboratory for analysis. The acid level is tested to provide pre warning of a potential compressor motor windings burn out. This is because acid in the compressor oil rots through the electrical insulation on the motor windings. The presence and quantity of white metal and yellow metal is analysed too. This is a window through to a component starting to wear inside the compressor.
0161 370 7193
The compressor in the photo is a screw compressor. It operates with ammonia refrigerant. This refrigerant is usually used for low temperature applications, mainly associated with food production. This compressor, however, has a 1° refrigerant saturation and is used to cool computer rooms. Common causes of compressor failure on this kind of compressor are:
The various compressor components are sealed together using ‘o’ rings or paper gaskets. ‘O’ rings are especially prone to leaks due to work hardening and flattening of the sealing face of the ‘o’ ring. The system can be pumped down and the compressor valved off. Then, our lift and shift team can remove the compressor to our remanufacturing facility for strip down.
The mating surface of a shaft seal has a mirror smooth finish. This is to reduce friction and aid with a better seal. Over time, this starts to wear, causing an ineffective seal and a leak of refrigerant and oil. A service visit can be arranged to change the shaft seal on site. The shaft couplings can be split, the shaft seal can then be removed and replaced. A quick job, then the machine is up and running again.
This is an electronic device with a slide attached to the moving compressor slide valve. The device has a start and an end position programmed into it during commissioning. The potentiometer converts the slide valve position, usually into a 4-20mA signal which is fed back to the chiller PLC. They are prone to reading out or the reading being jammed in one position. This results in a trip out from the controls, as the controller is not able to determine the true position of the compressor slide valve. We have an off the shelf stock of slide valve potentiometers for the various compressor range. A service visit can be arranged to replace the part after diagnosis has been carried out.
0161 370 7193
Centrifugal compressors are a very reliable kind of compressor but when they go wrong, they can go wrong in a big way. Compressor overhaul is expensive, this can be carried out onsite, or a better option is a lift and shift to our remanufacturing facility. Proximity sensors are usually fitted to monitor the distance between the impeller and the casting. This is an added protection along with the other sensors and transducers around the compressor.
We are on account with Micro Control Systems- an American company who specialise in building panels to order for specific chiller compressors. We easily fit this control system to any compressor to control the loading of the vanes in accordance to the available load from the process. The control panel has previously been fitted to other machines of the same model number, so any teething issues have already been ironed out. Maximus Chillers can achieve seamless operation of your plant.
Newer centrifugal compressors are oil free so as to eliminate any of the service issues relating to oil. There are a substantial amount of compressors, however, that use oil to lubricate the bearings. This kind of compressor, if properly serviced, can last for 50 years. The oil system picks up impurities which are caught by various filters. These filters can be changed or cleaned according to the prescribed service schedule. Our engineers make sure that spares are ordered and kept onsite prior to a visit.
Our visits and ongoing upkeep of your plant saves money. Money spent as a preventative measure saves so much more money in the long run. With competitive prices on specialist internal compressor parts- Maximus Chillers completes the picture. When compressor failure occurs, you are in safe hands with years of industry experience invested in each of our engineers.
0161 370 7193
With high discharge pressure, there is a corresponding increase in discharge temperature. This means that the compressor is operating beyond its recommended values. The cause of this is often a poorly maintained condenser. Especially on industrial chillers, there can have been gaps in the schedule where the condenser was not correctly serviced. This condition is often rectified easily by an onsite engineer by giving it a brush down. Where the fins are bent over- we carry a specialist tool to straighten them back out- how they came out of the factory. We also use different formulas of chemicals to rinse the various kinds of dirt from deep within the fins.
Some chillers are used where very high water temperature can come back from the process if the chiller were to be off line for a short period. Usually, this happens in factories where certain industrial processes are being carried out. When the onsite engineers start the plant back up, the chiller experiences a high heat load to deal with.
Maximum operating pressure expansion valves limit the pressure in the evaporator to a given level, regardless of the available heat load from the process. They do this by having a limited amount of liquid refrigerant in the bulb. When this runs out, the power element cannot push the orifice open any further- thus limiting the suction pressure. This is important to prevent scroll compressor failure as it prevents putting added strain on the compressor motor windings due to high suction pressure.
Where there is a shortage in refrigerant, there follows a low oil level condition. The refrigerant mass flow rate, carries the oil around the system and back to the compressor. This is greatly impaired when the chiller is short of gas. The oil cools the compressor and lubricates the shaft bearings. These bearings and other internal components wear down and seize causing failure. Maximus Chillers can put together a package to minimise chiller compressor failure.
Visit Wikipedia to read more about impellers which are used in centrifugal compressors | Click Here
A chiller service company can carry out diagnosis even when a wiring diagram is not available- our engineers can trace the wiring around the chiller.
News Article No.3
This often aids with diagnosis even when there is a wiring diagram, as to have your eyes on a component often makes more sense than a symbol. In any case, our engineers carry out system testing with Fluke multimetes and ammeters. We carry a range of thermocouples and probes to be used in conjunction with our calibrated digital thermometers. We use these along with comparators to carry out leak testing…
According to the frequency dictated by the quantity of refrigerant, we use the above test equipment to carry out F-gas leak testing. First, we have a visual look around the chiller for a sign of a gas leak. All parts of the pipework and system components are inspected. Then, we carry out a full refrigerant diagnosis to determine that the refrigerant system is operating with a full charge of refrigerant. The report for each chiller being completed and filed in the onsite F-gas leak register. A history can be built up to assess the serviceability of the plant and the frequency of leaks.
Where intermittent faults are concerned, on going system monitoring is required. If the job is not progressed on each visit, there is little point in a call out. We carry out tests during monitoring and ensure that the wiring is tight. Hopefully, waiting for the fault to occur whilst next to the machine. Alongside this, we rely on a report from the end user, as regards, the symptoms and the circumstances of the chiller when the fault occurred. From this we extrapolate the diagnosis and decide the next step to take. This may be to attempt to move the fault to another machine or, at least eliminate one thing each visit.
0161 370 7193
These have a rolled steel shell, welded down the seam with and end plate on either end. The water system pipes can be bolted to the sides or the end. The endplate can be removed for access to the waterside of the tubes. A strainer is fitted to the inlet to catch any foreign objects that may have been carried around the water system. Inlet and outlet gauges are fitted for the monitoring of the water system readings during a service visit. On larger chillers the screw or centrifugal compressor is mounted directly on top of the evaporator- sucking directly off the top of a flooded evaporator…
This kind of evaporator has the refrigerant in liquid form on the outside of the tubes. These are a rack of copper tubes extending through the length of the shell. The warmer process water running through the tubes causes the refrigerant to boil off. A sight glass is usually available to check the state of the refrigerant evaporating on the copper tubes. The suction from the top of the evaporator goes round a baffle so as to prevent the slug back of liquid refrigerant into the compressor. The refrigerant flow into the evaporator is controlled by the expansion valve…
This takes the form of a fixed size orifice on the liquid line in between the shell and tube condenser and the flooded evaporator. The size of the orifice previously being calculated to match the mass flow rate of the refrigerant dictated by the compressor. Some newer systems have a variable orifice for the more efficient running of the plant. This is controlled electronically along with the loading of the compressor, relative to the available load condition.
Smaller DX evaporators are usually multi system. This gives an N+1 redundancy of the plant. Indeed, when one side of a 2 system evaporator is having service work carried out, the other side continues to operate normally. Thinking ahead and allowing for additional capacity is essential when the application is critical, such as, a data centre or a hospital. When a redundant system comes online due to a failure- getting the system back up and running is a matter of urgency. For this we offer same day delivery of parts and a fully stocked mobile workshop.
0161 370 7193
Various configurations are employed to ensure good air flow through the chiller condenser fins. The most popular being a ‘v’ condenser as the surface area is increased with this design. Powerful fans are used to reject the air and heat upwards and away from the chiller. Where system location causes the recirculation of air, duct work can be fitted to direct the air away from the chiller.
A popular kind of pressure transducer used on condensers is Johnson Controls. These can be bolted onto the refrigerant discharge pipe to sense the system pressure. They have a 5vdc input that comes into the transducer on a red wire, a black wire is the ground and a white wire is the signal back to the fan speed controller. The transducer has a minimum to maximum range, so a chart can be used to determine if the signal is reading back correctly. On chillers where the transducer is wired directly in the controller- calibration can be carried out to offset the readings.
Another kind of pressure transducer is the 4-20mA type. It sends a mA signal back to the controller or the fan speed controller. 4mA is the minimum position, so this relates to the minimum of the transducer pressure range.
R134a refrigerant operates at a lower pressure in a condenser than the other commonly used HFC refrigerants. If you were looking for a chilled water set point of 6° in the UK ambient for example, the R134a refrigerant saturation on the high side of the system would be around 36° Latent heat from the water system and heat added into the refrigerant from the compressor are rejected from the condenser. As the refrigerant passes down the condenser tubes, cool air blowing across the outside of the tubes, cools the refrigerant vapour down through the latent heat phase and into a subcooled liquid.
0161 370 7193
This kind of compressor has a lower volumetric efficiency compared with the positive displacement compressors below. This is because the refrigerant is compressed using centrifugal force off the tip of the impeller, instead of being mechanically compressed. The advantage of this kind of compressor is a high mass flow rate of refrigerant. These compressors are used in factories where a large amount of chilled water is required to cool the process. They are also used in countries where district cooling is used. The chillers are arranged in rows in a chiller hall and are piped into the district cooling loop.
Oil used to lubricate the bearings is also used to create a seal between the rotors. Computer aided design (CAD) software and computer numerical control (CNC) grinding machines are used in the construction of screw rotors. The shape of the rotors is designed to compress the refrigerant along the screw. The length of the screw that is available to compress the refrigerant can be adjusted with a slide valve. Any stage of loading between 0- 100% can be achieved. This is regulated with a slide valve potentiometer. Screw compressors are very reliable and have a long service life. They also have a low vibration reading which ensures a lower instance of refrigerant leaks around the compressor.
A service free compressor. Service free assuming that the rest of the system is functioning correctly. This kind of compressor relies on oil migration around the system. The oil is entrained along the inside of the pipework, around the system and back to the compressor. An oil level sight glass is fitted into the body of the compressor at the required level. Refrigerant shortage can cause the oil to stay in the bottom of the evaporator, causing a low oil level condition in the compressor. Chiller service companies can be scheduled to attend site to drain the oil, then pump new oil into the compressor.
When any of the above compressors fail, you are in safe hands with Maximus Chillers. We have the capability to lift and shift the compressor to our remanufacturing facility for a full overhaul. The reason for the failure is diagnosed to ensure the new compressor does not fail for the same reason. Improving the reliability of your plant and extending its life is what we are all about- if we can reduce your service costs- that makes us happy! All temperatures and pressures are recorded to ensure the replacement compressor goes into seamless operation.
Any Chiller- Any Problem- Any Part- Any Refrigerant- Anywhere- The MAXIMUS ADVANTAGE™
Chilling Plant Service
Read more about pressure sensors on Wikipedia | Click Here
Category : Chiller Reconditioning
As a chiller parts supplier, all kinds of centrifugal compressors are remanufactured in our workshop. With an over head gantry crane and specialist equipment to hand- Maximus Chillers completes the picture.
Screw compressors are remanufactured on the bench. With compressed air and bearing tools- our skilled screw compressor technicians are seasoned in high tolerance measurements.
We have a range of off the shelf Copeland compressors for a fast lead time on process chiller repairs.
When the condenser on an air cooled chiller is in poor condition- our site survey team will attend to measure up for a new bespoke condenser.
This type of condenser is used on water cooled chillers.
This is the most popular type of evaporator for large chillers. The low temperature refrigerant is on the outside of the tubes in liquid form. The water is pumped through the tubes, releasing heat from the process into the refrigerant. This is latent heat as the liquid refrigerant boils off into a vapour.
0161 370 7193
We have all the sizes of anacondas on the shelf in our stores. This saves on the delivery time to site when your process if off due to the chiller. Maximus Chillers will get you up and running- fast!
For when things go wrong… we stock a solvent based flushing agent which is blown through the system with nitrogen.
These are another term for a subcooler. If the refrigerant is further subcooled after the condenser- the system will run more efficiently.
We can make temporary repairs to faulty pressure transducers using our test equipment. This will keep your plant running while the part arrives onsite.
A full selection of refrigerants are available in our stores including: anhydrous ammonia, R407c, R134a and R410a.
Low, medium and high viscosity oils in 5ltr cans and 20ltr drums are ready for shipping from our storage area.
Any Chiller- Any Problem- Any Part- Any Refrigerant- Anywhere- The MAXIMUS ADVANTAGE™
To read more about chiller evaporators- click the Tag at the top of the page.
Chiller Refurbishment Company
Read more about the centrifugal vapour compressor at the Institute of Refrigeration | Click Here
Category : Chiller Technology
At the beginning of the year we completed centrifugal chiller maintenance for one of our customers in America. A last overseas trip for the moment given the current world lockdown. The chillers in the photo chill water that is pumped around a university campus.
The plant has a water cooling shell and tube evaporator and a water cooled shell and tube condenser. It has been designed according to the N+1 principle: N being the amount of cooling required and 1 being that same amount of cooling again. Each chiller has enough capacity to satisfy demand. Given the large size of the campus, this principle was critical to keeping the University functioning should system failure occur. The chiller on the right was the lead chiller on arrival. After taking detailed readings during the maintenance, our engineer switched that chiller over into being the lag chiller and took readings from the chiller on the left. He rotates the lead/ lag of the chillers on each visit to balance the run hours of the compressors.
Centrifugal chillers have a lower volumetric efficiency compared with positive displacement compressors such as screws and repips. This is because the impeller does not mechanically compress the refrigerant like a piston in a reciprocating compressor. This kind of compressor relies on centrifugal force to spin the refrigerant off the tip of the impeller and onto the next stage. The refrigerant is then discharged from the compressor.
0161 370 7193
The above is more than compensated for with a high mass flow rate. That is to say: a high volume of refrigerant circulates around the system at its operating density. A large capacity machine is cost effective when considering energy efficiency and centrifugal chiller maintenance costs.
The gantry crane in the picture is available to aid with the lift and shift of the compressor, should compressor failure occur. Maximus Chillers are specialists in the overhaul of centrifugal compressors. We can arrange the lift out, transportation, strip down and reassembly of your compressors. All of our strip downs come with a 12 month warranty to give you peace of mind and confidence in our ability.
Air Cooled Chiller Planned Maintenance
Follow this link to read about centrifugal compressors at The Engineering Mindset | Click Here