Category : Chiller Components
System Testing for Chiller Compressors
Chiller compressors fail often as a result of ineffective servicing and system testing. At Maximus Chillers, we carry out extensive tests during our visits to ensure that small problems are resolved before they become big problems. If we notice a reading starting to become abnormal, we can carry out the diagnosis and then remedy the problem. Some of the compressor readings we monitor are:
Temperature of Chiller Compressors
The suction, discharge, motor windings and bearing temperatures are recorded for comparison to previous visits. These are often available in the PLC for the chiller, or our engineer can take the readings with his test equipment. Problems with the oil cooler can be the cause of higher compressor temperatures, the system running outside of its nominal operating conditions is another reason. Magnetic drive systems have an advantage as they do not use oil.
Portable vibration sensors are carried in of each of our company vehicles. This is an accelerometer to measure vibration. Along with other system readings, we keep an on going record of the vibration levels around the compressor. When internal components are coming out of alignment due to wear, this causes an out of balance condition in the compressor. This, in turn, causes a knock on effect- causing other components to go out of balance. Catching this condition early will prevent a compressor smash up resulting in the replacement of expensive internal components.
Oil Analysis for Chiller Compressors
Another way of preventing big problems from occurring is periodic compressor oil testing. Samples are taken, usually on alternate visits, which are sent off to a laboratory for analysis. The acid level is tested to provide pre warning of a potential compressor motor windings burn out. This is because acid in the compressor oil rots through the electrical insulation on the motor windings. The presence and quantity of white metal and yellow metal is analysed too. This is a window through to a component starting to wear inside the compressor.
0161 370 7193
The compressor in the photo is a screw compressor. It operates with ammonia refrigerant. This refrigerant is usually used for low temperature applications, mainly associated with food production. This compressor, however, has a 1°C refrigerant saturation and is used to cool computer rooms. Common causes of compressor failure on this kind of compressor are:
Leaking Castings on Chiller Compressors
The various compressor components are sealed together using ‘o’ rings or paper gaskets. ‘O’ rings are especially prone to leaks due to work hardening and flattening of the sealing face. The system can be pumped down and the compressor valved off. Then, our lift and shift team can remove the compressor to our remanufacturing facility for strip down.
Leaking Shaft Seal
The mating surface of a shaft seal has a mirror smooth finish. This is to reduce friction and aid with a better seal. Over time, this starts to wear, causing an ineffective seal with a leak of refrigerant and oil. A service visit can be arranged to change the shaft seal on site. The shaft couplings can be split, the shaft seal can then be removed and replaced. A quick job, then the machine is up and running again.
Slide Valve Potentiometer
This is an electronic device with a slide attached to the moving compressor slide valve. The device has a start and an end position programmed into it during commissioning. The potentiometer converts the slide valve position, usually into a 4-20mA signal which is fed back to the chiller PLC. They are prone to reading out, or the reading being jammed in one position. This results in a trip out from the controls, as the controller is not able to determine the true position of the compressor slide valve. We have an off the shelf stock of slide valve potentiometers for the various compressor range. A service visit can be arranged to replace the part after diagnosis has been carried out. The controls operate the loading and unloading solenoid valves to change the position of the slide valve.
0161 370 7193
Centrifugal compressors are a very reliable kind of compressor but when they go wrong, they can go wrong in a big way. Compressor overhaul is expensive, this can be carried out onsite, or a better option is a lift and shift to our remanufacturing facility. Proximity sensors are usually fitted to monitor the distance between the impeller and the casting. This is an added protection along with the other sensors and transducers around the compressor.
We are on account with Micro Control Systems- an American company who specialise in building panels to order for specific chiller compressors. We easily fit this control system to any compressor to control the loading of the vanes in accordance to the available load from the process. The control panel has previously been fitted to other machines of the same model number, so any teething issues have already been ironed out. Maximus Chillers can achieve seamless operation of your plant.
Oil System for Chiller Compressors
Newer centrifugal compressors are oil free so as to eliminate any of the service issues relating to oil. There are a substantial amount of compressors, however, that use oil to lubricate the bearings. This kind of compressor, if properly serviced, can last for 50 years. The oil system picks up impurities which are caught by various filters. These filters can be changed or cleaned according to the prescribed service schedule. Our engineers make sure that spares are ordered and kept onsite prior to a visit.
Our visits and ongoing upkeep of your plant saves money. Money spent as a preventative measure saves so much more money in the long run. With competitive prices on specialist internal centrifugal compressor parts- Maximus Chillers completes the picture. When compressor failure occurs, you are in safe hands with years of industry experience invested in each of our engineers.
0161 370 7193
These are some issues affecting a scroll compressor:
High Discharge Pressure
With high discharge pressure, there is a corresponding increase in discharge temperature. This means that the compressor is operating beyond its recommended values. The cause of this is often a poorly maintained condenser. Especially on industrial chillers, there can have been gaps in the schedule where the condenser was not correctly serviced. This condition is often rectified easily by an onsite engineer by giving it a brush down. Where the fins are bent over- we carry a specialist tool to straighten them back out- how they came out of the factory. We also use different formulas of chemicals to rinse the various kinds of dirt from deep within the fins.
High Suction Pressure on Chiller Compressors
Some chillers are used where very high water temperature can come back from the process if the chiller were to be off line for a short period. Usually, this happens in factories where certain industrial processes are being carried out. When the onsite engineers start the plant back up, the chiller experiences a high heat load to deal with.
MOP Expansion Valves
Maximum operating pressure expansion valves limit the pressure in the evaporator to a given level, regardless of the available heat load from the process. They do this by having a limited amount of liquid refrigerant in the bulb. When this runs out, the power element cannot push the orifice open any further- thus limiting the suction pressure. This is important to prevent scroll compressor failure as it prevents putting added strain on the compressor motor windings due to high suction pressure.
Oil and Refrigerant Shortage
Where there is a shortage in refrigerant, there follows a low oil level condition. The refrigerant mass flow rate carries the oil around the system and back to the compressor. This is greatly impaired when the chiller is short of gas. The oil cools the compressor and lubricates the shaft bearings. These bearings and other internal components wear down and seize causing failure. Maximus Chillers can put together a package to minimise chiller compressor failure.
People also like this page:
Centrifugal Compressor Remanufacturing
Screw Chiller Compressor Maintenance
To read more about scroll chiller compressors hit the Tag at the top of the page.
Read more about impellers which are used in centrifugal compressors at Wikipedia