Category : Chiller Reconditioning
We recently undertook the job to carry out bespoke R407c chiller condenser retrofitting in the North West.
Rusted and Corroded Condenser
The old condenser looked alright on the surface- the fins were in good condition. The chiller condenser was 18 years old and when an attempt to repair a leak was carried out- the condenser leaked further along. This is because of the warming of rusted and corroded copper with an oxy-acetylene torch.
R407c Chiller 'V' Condenser Retrofitting
We arrived on site to measure up for the job. The ‘V’ chiller condenser being retrofitted was built to order. We manufactured an exact replica to the same specifications and sizes of the old one. The operating pressures and high pressure cut out limit were taken into account in the design and the use of materials.
0161 370 7193
Lift Out of the R407c Chiller Condenser being Retrofitted
On the day of the lift and shift we isolated the panel and checked it was dead, then we removed the panel and laid it on it’s front. This was to access the rivets behind the panel. These rivets, the ones on the other end of the chiller and around the lid were removed using a tool. The fans were disconnected and removed to make the lid lighter to lift off. Then, we attached slings to the chiller condenser and lifted both halves of the 'V' out.
Lift In of the Chiller Condenser being Retrofitted
This part we did not want to get wrong as the R407c chiller condenser being retrofitted was brand new and did not have a mark on it. A reverse of the removal- it fitted perfectly just the same as the old one. With the lid lifted back on and the fans in- time for brazing then the pressure test.
Pressure Test, Dehydration and Recharge
The pressure test was satisfactory so our engineer put the system on vac for dehydration purposes and the removal of non condensables. After a deep vacuum was achieved the system was recharged and run tested. No issues were found.
Chiller Refurbishment Supplier
Read more about air cooled condensers at the Institute of Refrigeration | Click Here