Centrifugal Refrigerant Compressor Service
12 month warranty on all of our remanufactured centrifugal refrigerant compressor services. We arrange the lift and shift, then repair and rebuild your refrigerant compressor in our workshop or:
Strip Down the Centrifugal Chiller Compressor Onsite
During the strip down, all the centrifugal chiller compressor parts are laid out on cardboard and pallets. These are arranged in a line on the workshop floor in the sequence that they were removed. The bolts are immersed in oil.
All parts are inspected for wear and tear and a list of required replacement parts is written.
When the parts come in, we re-build the compressor using new chiller industry gaskets and ‘o’ rings.
Centrifugal Chiller Compressor Bearing Overhaul
The clearance of the centrifugal chiller compressor bearing is checked with a gauge and the bearing is adjusted where necessary. Not enough oil lubrication will reduce its life.
The ‘Run-out’ of the Shaft
We check this with our instrument. If the shaft is not spinning true, this will also reduce the life of the bearing.
The rebuild is the reverse of the strip-down- all screws are tightened to the correct torque with a torque wrench. The compressor is then pressure tested and dehydrated with a vacuum pump.
The centrifugal refrigerant compressor is maintained by pumping in the correct amount of oil according to the technical bulletin for the compressor.
Centrifugal HVAC Compressor Casting Maintenance
Last but not least the centrifugal HVAC compressor (a term often used in America) is sanded down and repainted.
Any Chiller- Any Problem- Any Part- Any Refrigerant- Anywhere- The MAXIMUS ADVANTAGE™
Case Study of Centrifugal Compressor Strip Down
On an oil rig, we recently carried out a strip down of a centrifugal chiller compressor used for the liquefaction of hydrocarbons. The oil had previously been analysed and confirmed worn bearings. Also, the bearings were at the run hours to be changed. We shipped all the necessary equipment to the rig prior to the commencement of the job. The on site stores were impressive as they keep a full stock of supplies.
Multi Stage Centrifugal Refrigerant Compressor Remanufacturing
The refrigerant was HFC so we followed the procedure for breaking in, then started the remanufacturing. We lifted the lid off, then the centrifugal refrigerant compressor was stripped down (teardown in America) and inspected. The re-assembly began by fitting the bearings- with a rub with molybdenum disulfide, or moly as known by engineers. After the compressor was rebuilt- it was carefully run tested and re-inspected then it went into seamless operation.
What We Offer
Professionally remanufactured compressors to beyond manufacturer's recommendations with a 12 month warranty.
National and global service. No location is too far for Maximus Chillers.
Blue chip service that is second to none.
Schedule a site visit today!