Glycol Chiller Service, Maintenance and Repair
Maximus Chillers are a glycol chiller service and maintenance company that carries out fast and effective repairs. The pictures are of low temperature glycol chillers
Glycol is used in chillers as an anti-freeze where applications have a below (or near) zero temperature. Propylene is non-toxic and food safe. Prices are narrowing between propylene and ethylene, so customers are choosing it more often. Ethylene is toxic so it cannot be used in conjunction with food production. It tends to be used in dirty and very industrial applications. Brine is often used in the industry, usually for larger and colder applications
Glycol Chiller Maintenance
One of the things we check during a glycol chiller maintenance visit is the glycol condition. To do this we use an instrument to test, then adjust the glycol solution. See Case Study below
Water is used as a secondary refrigerant not because it is abundantly available on earth, but because it has very good thermodynamic properties. Water is very good at absorbing and rejecting heat. The only flaw is that water freezes at zero degrees. A call out can occur when the end user reports that the chillers are not doing anything. Sometimes, the onsite engineer can be testing and adjusting the glycol condition incorrectly. The fix is to pump out the water system to vessels and re adjust the glycol condition
Why Choose Us for Glycol Chillers?
When you are having a problem- our engineers are in their element with glycol chillers- they deal with problems all week! We will identify the fault correctly- so the repair goes easy
Any Chiller- Any Problem- Any Part- Any Refrigerant- Anywhere- The MAXIMUS ADVANTAGE™
The Contact Form is monitored and works so if you are busy drop us a line
Give us a bell on 0161 370 7193. We are more than happy to assist you with technical issues
Send an email to: email@example.com
What We Offer for Glycol Chillers
Glycol Chiller Repair
UK and overseas coverage
Same day delivery of parts direct to site
Dedicated glycol chiller maintenance engineers: we understand the water system as well as the fridge system
Glycol Chiller Service
Have you had your machine looked at recently? Chillers lose efficiency over time. We offer an expert glycol chiller service visit to sort out your problems!
Case Study of Glycol Chillers
A large -10 glycol chiller was having Low Pressure problems. After it had been off for a while it ran okay. Then 5 minutes into the run, however, the low pressure would start dropping off at an increasing rate until a LP trip occurred. The previous company had fitted an expansion valve and pressure tested the system. The onsite engineer said the glycol condition was okay "let me check with my instrument" our engineer said. As he thought- it was a glycol issue. A chiller repair was arranged
Schedule a site visit today!