Category : Articles
We at Maximus Chillers will optimise the efficiency and take years off the life of your plant with preventative chiller maintenance.
News Article No.9
Chiller Control Panels
The first thing our engineers check at the start of the maintenance is the chiller control panel. In here he checks:
Programmable Logic Controller
The alarm history is analysed in sequential order to build up a picture of the last maintenance period.
Settings and Timers
The various levels of password accessed menus are checked and adjusted for efficiency and to eliminate any spurious trips on the running of the chiller.
Compressor Run Hours
We make a note of the compressor run hours on our detailed Tick Sheet. Bearings on centrifugal compressors and valve gear on reciprocating compressors are changed at pre prescribed intervals as defined by the manufacturer. This is to prevent an expensive failure and the resulting remanufacturing of the compressor.
Preventative Chiller Maintenance of Electrical Safety Devices
Each one of these is popped from its holder and the continuity checked with a multimeter. This is maintenance the right way round, instead of run testing and following the fault back to the fuse.
Each of the breakers is tested to ensure it will function correctly when it needs to.
Residual Current Device
RCD’s work by detecting current leakage to earth. It monitors the difference between the live and neutral poles. As above these are tested on each visit.
Preventative Chiller Maintenance of Refrigerant Safety Switches
High Pressure Switches
The settings and dead band (the difference in pressure between cut out and cut in) are checked and adjusted on each visit. Sometimes due to malfunctioning controls or condenser condition, fans can be manually left off or can be forced on. Not the best running condition, but we will keep you up and running until we send out the new parts. Where this is a bespoke manufactured condenser, we have the best lead time available.
Low Pressure Switches
As above, the low pressure switches are checked and adjusted as need be. The seasonal and varying load conditions affect the saturation point of the refrigerant in the evaporator. This can cause untimely trip outs when the plant is otherwise running in optimum efficiency.
0161 370 7193
Coefficient of Performance during Preventative Chiller Maintenance
The coefficient of performance is the cooling effect compared with the electrical energy supplied to the chiller. It is represented in a ratio, for example 6:1. That is six times more cooling effect compared with the electricity supplied. The higher the cooling effect relative to electricity supplied, the lower the cost in electricity. The ratio is often divided by 1 to show as just a number- in this example 6. The cooling effect is measured in kj/kg and the electrical supply is represented in kw/h.
A chiller system would have a COP of less than 1 if not for latent heat. Exploiting this hidden heat when both evaporating and condensing the refrigerant is one of the founding principles of the basic refrigeration cycle. It takes a lot of heat added to the system to get the refrigerant to boil, then the same amount of heat is rejected from the condenser in the liquification of the refrigerant.
A lot of basic things routinely drag down the efficiency of a chiller system. Just with the effect of our engineer attending site to carry out the maintenance- he will keep the COP optimised. Here are some of the system checks and procedures he carries out:
When a compressor never goes off due to refrigerant shortage, there is a dramatic increase in electricity consumption. Also, the system will not have very much cooling effect. Continuing like this will cost more money and achieve little.
Basic condenser maintenance will improve the subcooling values. These readings will be taken at various load and ambient conditions at different times of the year. This is so we can build up an understanding of the plant. We carry a wide range of chemicals for the maintenance of your condenser. These chemicals are carefully selected so that they do not damage the condenser causing leaks. Condenser fans also cause a poor COP:
0161 370 7193
Preventative Chiller Maintenance and Condenser Fans
With some basic chiller designs, the chiller condenser fans come on and off forwards and backwards at different pressures. This means that when other fans have failed, or are stuck going backwards- the one on the end comes on with the higher pressure then blows to earth. This is due to the ingress of water in the year it did not run.
The above design means that there are fluctuating pressures in the condenser. This causes continuous expanding and contracting of the copper tubes. These copper tubes rub against the steel frame which is holding them in place- causing reoccurring leaks. Another reason for repeated leaks on the condenser is the vibration issue of the fans banging on and off. Add into this equation a cheap, flimsy frame that develops its own resonance- you then have an un ending problem.
Preventative Chiller Maintenance with Fan Speed Controllers
Part of what we call the MAXIMUS ADVANTAGE™ Any Chiller- Any Problem- Any Part- Any Refrigerant- Anywhere is that we can source any fan speed controller from our fast supply chain. This remedies the problem, as fan speed controllers bring all the fans on together at different speeds. Therefore, extending the lifespan of the fan and maintaining an efficient coefficient of performance.
Most air cooled chillers use axial fans. They suck the air through the condenser and reject it upwards and away from the chiller. Ducts are often fitted to help this process. Scaffolding is erected to provide safe access to engineers.
Radial fans are also called centrifugal fans or blowers. They are very popular in server rooms where air is blown down into a mezzanine floor and up through the racks. They are also used outside in chillers where they blow out and away from the chiller. They are usually driven by belts which require regular inspection and maintenance.
0161 370 7193
Preventative Chiller Maintenance and R134a Refrigerant
In the photo, the controller shows R134a refrigerant and the 8.3° of superheat as calculated by the program. This superheat may look at first to be okay, but when considering the compressor loading and expansion valve- it points towards a system issue. Our engineers diagnose if the issue is related to a component or a refrigerant shortage.
HFC refrigerant which has a chemical name of Tetrafluoroethane or CF3CH2F. It has low toxicity which is good for the health and safety or our engineers. It is not combustible, but other chemicals are made as a result of a fire. It is non corrosive too, which extends the lifespan of the pipework and components around the system.
Centrifugal Drop In
This refrigerant is widely used as a replacement for HCFCs, such as, R22 used in centrifugal chillers. It is only one fluid, where as the other popular HFC refrigerants are blends. These blends fractionalize in a flooded condenser or evaporator. That is to say: one or two of the refrigerants in the blend separate out and do not continue their cycle around the system. The chiller now has the wrong refrigerant circulating around the system for the application temperature. Extreme running faults follow, such as, ice on the compressor, suction pipe and expansion pipe. This is as a result of the refrigerant pressures and temperatures being outside of nominal conditions.
Global Warming Potential
A global warming potential of 1430 is considered to be high. Therefore, the refrigerant is being phased down to 21% by 2030 in line with F-gas guidelines. These guidelines are in accordance with the European Union and the Kyoto Protocol. Because of the regulations for the handling of fluorinated gas, our engineers attend college to learn how to decant the refrigerant safely. We then ship it to the recycling centre for disposal. A waste carrier note being completed each time to track the refrigerant from dispatch to disposal. Finally, F-gas leak tests are carried out and recorded on each visit. Maximus Chillers completes the picture.
Air Cooled Chiller Planned Maintenance
To read more about chiller control panels hit the Tag at the top of the page.
To watch a video about chiller efficiency and the coefficient of performance | Click Here