Process Chiller Service
Category : Chiller Technology
Maximus Chillers has just carried out process chiller service to a flooded evaporator. The refrigerant seal on a four bolt, flanged coupling had been found to be leaking liquid refrigerant. There was no possibility to valve off that section of the machine, as the flooded evaporator is the storage vessel for all of the charge of the system in its liquid phase.
Refrigerant Decant for Process Chiller Service
Our high capacity pump out unit was set up next to the machine to carry out process chiller service. 55 kg of refrigerant was recovered in a short time into our recovery cylinder. This refrigerant was collected for recycling after the job was completed.
Process Chiller Refrigerant Leak Service
The flanged coupling was unbolted and the failed refrigerant seal was removed. The new seal was fitted from our full range of sizes that we keep on the shelf in our stores. Our engineer bolted the flanged coupling back up to the correct torque setting.
Pressure Leak Test
A nitrogen pressure leak test was carried out to ensure the integrity of the system with the result being a pass.
As the system was open to atmosphere, air had got into the system which carries moisture content. The moisture and non condensables were removed down to a near perfect vacuum using one of our high capacity vacuum pumps.
0161 370 7193
Charging of Refrigerant
The photo shows the charging of a cylinder of refrigerant into the system in its liquid phase. The cylinder has a dip tube fitted for ease of cylinder handling. Once the pressure in the system and the cylinder equalized, remaining refrigerant was drawn into the system during the operation of the plant.
The sight glasses and level glasses were found to be at the optimum level under the normal running conditions of the process chiller. As it is a flooded system, there was found to be a low superheat value. A high subcooling value was achieved with the use of a subcooler. Our engineer monitored a full cycle of an hour and a half: compressor temperatures and oil level were found to be within normal operating limits.
Remote Service Monitoring of Process Chiller
The service of this process chiller can be remotely monitored via a data uplink through the internet. Our office continued to monitor the plant for some days as it went into seamless operation.
Chilling Plant Service
Follow this link to purchase BESA pressure testing technical bulletin Click Here